Frontpanel of the design
Terminals inside the device
Connect the 230V power supply at the terminals "Netz L, N". A version for 24V supply is also avalable.
Connect the current - loop resistor at the terminals "TERM. RESIST". The function of the resistor is to keep the remote current in local mode to prevent a error message of the remote controler device. It should be between 10 Ohm till 800 Ohm.
Connect the remote current source at the terminals "Input (REM)".
Connect the device that is current controlled at the terminals "OUTPUT (USER)". The internal current loop resistant of the device can be 0 Ohm till 800 Ohm.
Attention: Check the polarity! Don't exchange + with -.
Power supply: 230V / 50Hz, +-15V, +-5Hz.
Technical Data des DIGISOL
Remote termination resistor: 10 Ohm till 1 K Ohm (like the remote current source needs).
Termination resistor of the controlled device: 10 Ohm till 800 Ohm.
Housing protection: IP65.
The power supply is galvanic isolated from the control current terminals.
Attention: While the key is between the modes the "OUTPUT (USER)" terminals are not connected. If you move the key in normal speed (not to slow) this is only for a view ms. The LED´s are both off in this state. This prevent a connection between the "Input (REM)" terminals and internal local source.
Block diagramm the internals
Here you see the principal block diagram of the device and the connections:
Downloads Weitere Dokumente und Files